Are used to remove suspended solids from water and wastewater. Because they have one layer of filters media, media filter remove only relatively large solids (normally in the range of 40 micron and larger). The effective size of each granule of sand typically varies from 0.35mm – 1.2mm. Larger granules yield coarser filtration. Finer granules yield finer filtration.
- Irrigation water
- Storm water
- Cooling water
- Swimming pool water
- Water in fountains and other features
Removing suspended solids smaller than 40 microns requires filters with either two or three layers of filters media. These are referred to as dual-media filters or multi-media filters. When sized properly and with the correct configuration of filter media, these sand filter can remove suspended solids as small as 5 micron.
Units are skid-mounted, factory assembled, wired, and tested, and delivered ready for installation. Piping, valves, filter media, pressure gauges and accessories are included with filters systems. Solar power, media air scour, and rinse cycle are available as options. Filters systems are engineered to require little maintenance. A separate source of water supply or a pump for backwash are seldom needed.
Sand filters are typically used for:
Design Features of Sand and Multi-media Filters:Solar power, media air scour, and rinse cycle are available as options. Filters capacities are from 5 GPM to 14 MGD. Chemical injection packages, settling tanks, clarifiers, and disinfection units are also
- 8 in. to 12 ft. diameter vessels
- Automatic or manual operation
- All steel construction (mild steel, 304 and 316 stainless steel)
- Stainless steel vessel internals
- ASME code or non-code vessels
- Hydraulic, pneumatic or electric valves
- High pressure and temperature options
- Class 1, Div. 1 or 2 preparation